1、 Precautions during pulling out and pushing: 1 / 4 drawer and 1 / 2 Drawer (black):
When pushing the drawer inward, before pushing the drawer, put the drawer flat, push it back and forth on the slide rail for a few times, confirm that it has fallen into the slot, and then push it. (if there is no slot, it will be difficult to pull out the drawer after it is pushed in. Because the inlaid partitions on both sides of the drawer block the cabinet frame and cannot be pulled out, the partitions and primary plug-ins on both sides of the drawer will be damaged
1. Pull out the upper and lower drawers, press the clamping point of the mosaic plate through the gap with a long screwdriver, and then pull it out. If it is pulled out hard, it will inevitably lead to the damage of the drawer frame.
Since both the upper and lower drawers are inevitably running during startup or normal operation, it may not be allowed to pull out the drawers, so it is troublesome to deal with it. Therefore, pay attention to the application of this method during power transmission, so as to be anxious but not urgent. Operate according to the normal sequence, reduce the failure time and avoid affecting the production
2. When pushing the drawer, push it with a force of 2 to 3 pounds when it is about 15cm away from the closing position. Do not push the full stroke of the drawer, which is very easy to damage the drawer; If the force is too small, it is not easy to push in place.
3、在抽屜推進后的操作順序：旋轉旋鈕(黑色)到試驗位置 按綠色啟動按鈕啟動(如接觸器吸合，運行指示燈亮，說明完好) 然后
3. Operation sequence after the drawer is pushed: turn the knob (black) to the test position, press the green start button to start (if the contactor is closed, the operation indicator light is on, indicating that it is intact), and then
Press and hold the knob (perpendicular to the axis of the knob) and rotate it directly to the running position with slight force. The red line of the knob is the vertical direction
If you don't press and hold the knob hard, the button will be damaged, resulting in failure of power transmission; When turning the knob to power on, it is sometimes difficult to rotate. At this time, check whether the drawer rotates in place. Whether the drawer frame and cabinet frame are jointed, even if there is a small distance of 1 to 2mm.
2、 Large drawer
1. The above 2 and 3 are also their points of attention.
2. Try pulling several times when pushing, because the secondary plug and primary main plug at the back of the drawer are not properly plugged into the frame matrix (pay attention when the drawer is replaced due to failure, because the types of connectors at the back of these drawers are different).
3. Sometimes when the drawer cannot be pulled out, it should be lifted up slightly and then pulled out (of course, at the same time). For example, the drawer at the upper end of the frame is difficult to pull out because this point is often ignored.
4. The operation of the secondary knob is the same as that of 1 / 4 drawer and 1 / 2 Drawer 3. Remember that only when the secondary knob reaches the operating position can the knob of the primary switch be pushed to the operating position, otherwise the knob of the primary switch will be damaged and will not be powered on.
5. The drawer can't be opened, mainly because the knob can't rotate.
This is the most important problem. Suppose the worst case: at this time, the drawer is often closed and in fault, and the production is eager to restore power transmission and open.
(1) in terms of cognition, don't be too superstitious about the indicated position of the knob, because it is only a mechanical chain after all. By constantly rotating the two knob positions (remote control, local knob and main switch knob), its position can be slightly deviated, and then try to open it. Generally, there is no problem in opening it.
(2) if the drawer cannot be opened and the production is in a hurry.
< strong > operation steps for quick reset and power transmission:
a: There is a small hole (lower right) next to the remote and local knob. Use a small screwdriver to extend into the small hole and press the baffle down.
b: There is a small hole on the left side of one-time closing. Similarly, use another small screwdriver to push it in and open it.
c: Unlock with two screwdrivers at the same time and open the drawer door.
d: Manually adjust the connecting rod in front of the primary switch (sometimes it can not be opened because the connecting rod is stuck) to disconnect the main switch.
e: Then confirm whether the mechanical connecting rod under the main switch has been released in place. If not, move it.
f: Unscrew the secondary switch button to the safe extraction position
g: Pull out the drawer, reset it and restore power transmission.
h: Only when the primary switch and the secondary switch are engaged in place, the drawer can be pulled freely and the switch can rotate smoothly.
We have been insisting on sharing MNS low-voltage drawer cabinet on the way http://www.8477k.com Truly solve the problems you need